View and Download Dixell XR20C installing and operating instructions online. Digital controller with off cycle defrost. XR20C Controller pdf manual download. View and Download Dixell XR20CX installing and operating instructions online. Digital controller with off cycle defrost. XR20CX Thermostat pdf manual. QVWDOOLQJ DQG 2SHUDWLQJ,QVWUXFWLRQV Digital controller with off cycle defrost. SET: To display target set point; in programming mode it selects a.
|Published (Last):||7 April 2007|
|PDF File Size:||12.97 Mb|
|ePub File Size:||1.75 Mb|
|Price:||Free* [*Free Regsitration Required]|
Parameter “IdF” controls the. DOWN To see the min stored temperature; dixel programming mode it browses the. Instrument XR20CX shall be mounted on vertical panel, in a 29×71 mm hole, and fixed using the special bracket supplied.
This manual is part of the product and should be kept near the instrument for easy and. Do not expose to water or moisture: Ensure that the wires for probes, loads and the power supply are separated and far. In case of failure or faulty operation send the instrument back to the distributor or to. It provides a relay output to drive the.
The “Hi” message will be displayed followed by the maximum temperature recorded. To print the manual completely, please, download it.
Enter text from picture: Add to my manuals Add. Consider the maximum current which can be applied to each relay see Technical Data. The digital input can operate as.
Dixell XR20C Electronic Digital Refrigeration Temperature Controller
Hold press the SET key for more than 3s, while the max. By pressing the 8 key again or by waiting 5s the normal display will be restored.
Page 2 Energy Saving cycle. Push the DEF key for more than 2 seconds and a manual defrost will. Don’t have an account? Check the supply voltage is correct before connecting the instrument. Push and immediately release the SET key: The instrument is fully configurable through special parameters that can be easily.
By pressing the 9 key again or by waiting 5s the normal display will be restored. Push the SET key for more than 2 seconds to change the Set point value. Page of 4 Go.
Ptb Map code Dixell S. CCS Set point for continuous cycle: XR20CX panel mounting in a 71x29mm panel cut-out Protection: To memorise the new set point value push the SET key again or wait 10s.
Dixell XR20C Installing And Operating Instructions (Page 5 of 5)
Don’t show me this message again. In case of fault in the thermostat probe the start and stop of the compressor are timed through. To confirm the operation the “rSt” message starts blinking and the normal temperature. Fit the probe where it is not accessible by the End User. In case of applications in industrial environments, the use of mains filters our mod.
Page 4 Ptb Map code Dixell S. The instrument shall not be sr20c for purposes different from those described hereunder. Installing and Operating Instructions.
The instrument must not be. To change the Set value push the 9 or 8 arrows within 10s. To display target set point; in programming mode it selects a parameter dixelp confirm. Push and immediately release the SET key vixell wait for 5 seconds to.
Defrost is performed through a simple stop of the compressor. Model XR20C, format 32 x 74 mm, is a digital thermostat with off cycle defrost designed for. Got it, continue to print. To see the max. The “Lo” message will be displayed followed by the minimum temperature recorded.
Each LED function is described in the following table. By pressing ‘print’ button you will print only current page. Comments to this Manuals Your Name.